WALL BRACKETS: The tested distance between wall brackets is 4m. Please note that is a maximal length. We recommend to use a wall bracket every 2m.
FREE END: The tested free end above the last support subject to wind is 2,5m for diameters 130mm and 150mm and 2,0m for diameters 180mm and 200mm. Please note that is a maximal length. We recommend to use a guy bracket and guy ropes or stiff supports if the free end is more than 1,5m.
Every connection above the last support except for regular narrow locking band should be additionally secured with a wide locking band.
|Name||Wall support 220mm - 380mm|
|Inside pipe||AISI 316L (1.4404)|
|Outside pipe||AISI 304 (1.4301)|
|Thickness inside pipe (mm)||0.4|
|Thickness outside pipe (mm)||0.4|
|Type of fuel||Wood & multifuel|
|Thickness insulation (mm)||30 mm|
|Distance to flammables (cm)||70mm in enclosed spaces and 50mm outside.|
|Temperature of use||600ºC continuous, 1000ºC peak.|
|Delivery time (working days)||1-3|
|Transport cost (total order)||From £8.99, Free delivery over £120.|
|(Compatible with) internal pipe diameter (mm)||200|