Building Regulations For chimney Installations
Any work that affects an existing chimney (including installation of a stove or flue liner) or creates a new chimney is considered building work and so comes under the Building Regulations.
The Government issue an Approved Document which contains practical guidance on ways of complying with the Requirements of the Building Regulations which deals with Combustion Appliances. In the UK Document J building regulations apply to flues and chimneys. It is important that these are adhered to for safety and legality.
Fitting a flue liner / chimney system yourself
You must notify Building Control prior to installing any chimney (unless you are approved to self certify, as are Hetas engineers)
You do not have to use a professional installer. If installing the stove into an existing fireplace/chimney and not using a new chimney liner then the installation is very straightforward for a person with average DIY skills. Installing a flexible chimney liner or complete twinwall system is a larger job and may involve ladders or scaffolding if external access to your roof is needed, but is still technically straightforward, no specialist knowledge or skills are required.
If you complete the work yourself then the local council Building Control should be informed and they can then inspect the work on completion to sign it off. Alternatively if the work is done by an installer who is accredited by one of the relevent Competent Persons schemes such as HETAS then they can sign off their work and provide you with a certificate.
Is not normally required. Installation of a stove and/or new flue system would not usually have anything to do with the local planning authority. If your propety is a Listed Building then permission may or may not be required. If you intend your new flue pipework to run up the outside of an external wall then depending on the position (e.g. side or front of house) you may need to check with the local Planning Department.
Do I need to line my existing chimney?
Most houses built after 1964 should have a concrete/clay inner liner in which case you probably don't need to reline unless there is a problem with your existing system.
Older houses will normally just be exposed brick inside - it is not a legal requirement to line these older chimneys unless they are leaking, but there are often advantages to lining such as increased draw, piece of mind of having a sealed system top to bottom, reduced risk of chimney fire or leakage etc.
The existing chimney/flue should be swept clean before any stove installation and checked for condition and correct operation. A smoke pellet should be burned at the bottom to check for any leaks or blockages. Your local chimney sweep should be able to advise on your chimney condition if you are not sure.
We always advise that chimneys in older properties should be lined.
You must notify Building Control prior to installing any chimney (unless you are approved to self certify, such as HETAS engineers).
Chimney design rules
- The minimum chimney height recommended for minimum performance of wood burning and multi fuel appliances is 4.5 m from the top of the appliance to the top of the chimney.
- The distance between the cowl of the flue and the adjacent roof/wall/structure should be higher than 2.3 mtr.
- A maximum of 4 bends (up to 45º angle) is allowed. In case of 4 bends; a sweep door in between the 2 outer bends is required.
- In case of an offset; a maximum of 20% of the flue length can be non - vertical (best practice).
Most solid fuel appliances in the UK have either a 5" (130mm) or 6" (150mm) flue outlet on the top or rear of the appliance. You will normally then use the corresponding sized vitreous enamel flue pipe for the first section of flue from the stove to take you into the chimney. From that point you will then usually have to change to a minimum 6" (150mm) flexible chimney liner or rigid insulated flue system. If you order a flexible liner kit or full twinwall flue system from us it will come with the suitable adaptor to connect to the 5" or 6" enamel pipe. That applies to most solid fuel appliances. The exception is for DEFRA Approved stoves which have a 5" (130 mm) flue outlet. They can legally be used with a 5" (130 mm) chimney liner or full flue system as they produce less smoke particles than other stoves.
Note: All installations are to be done according to UK Building Regulations, Document J. The tips on this page are meant to help you to do so, but in no way should be considered as a replacement of the instructions and rules of document J.
What other people are saying about us:
"Loved the support"
"Very rapid delivery and well packed. All items in excellent condition. Thanks dad for the installation!"
Carolyn Mckinnon - Bath
"Easy job of just a few hours..."
H. T. Edwards - Birmingham